Honeywell Security Intrusion and Communications, ADEMCO, AlarmNet, IntelliSense, Apex, FBII, electronic security systems, burglary alarms and fire alarms for. Installation manual for the Honeywell wireless three-zone sensor. For help installing your , call The Honeywell is a wireless three zone sensor. Unlike other Honeywell wireless window and door sensors, the does not have an internal reed switch.
|Published (Last):||18 October 2008|
|PDF File Size:||16.39 Mb|
|ePub File Size:||11.13 Mb|
|Price:||Free* [*Free Regsitration Required]|
By pressing ‘print’ button you will print only current page. Complain wrong Brand wrong Model non readable. Don’t have an account? Risk of fire, explosion, and burns. No increase or alteration, written or verbal, of the obligations of this Limited Warranty is authorized. Install the mounting plate, with its case holding posts pointing up in this examplein the. The open slot at the other end of the unit cannot be used as a cover pry-off. Recommendations must be included for a specific.
For UL installations with fire zones, the position 4 ON setting must not be used. The has its ademck unique identification codes permanently assigned during manufacture. If concealed wiring is to be used, feed the wires through the concealed wiring entry hole at.
Seller shall have no obligation under this Limited Warranty or otherwise if the product s is altered or improperly repaired or serviced by anyone other than Honeywell factory service. Remove the transmitter’s adekco if not already off as described in Mounting Step 1.
Although two holes are provided in the unit that would permit mounting directly to a surface holes “A” in Diagram 2it is recommended that the mounting plate be used, as described below, for ease in removing the unit for servicing should it become necessary. To replace the cover, engage the hooks along one edge and snap shut. Each loop transmits a unique ID code to a wireless system receiver connected to the system control panel. Surface wiring should enter via the thin “breakout” area provided in.
Customer understands that a properly installed and maintained alarm system may only reduce the risk of a burglary, robbery, fireor other events occurring without providing an alarm, but it is 55817 insurance or a guarantee that such will not occur or that there will be no personal injury or property loss as a result.
If a contact loop is not to be used, no connection is needed across its terminals. While the transmitter is being enrolled by the control, all DIP switch positions should. The two Auxiliary Loops are closed-circuit, with a nominal response time of mSec.
Honeywell ADEMCO User Manual | 2 pages
Regular maintenance and inspection at least annually by the installer and frequent testing by. Except in the case of the position 4 ON setting, the Auxiliary loops are not affected by.
Mounting For proper orientation of the unit in relation to its wall mounting plate and the loop wiring, read all of this section before installing the unit. The unit may, however, be installed in any direction, as long as the relationship of the unit to its mounting plate is maintained.
The should be treated as “RF” i. Disengage the supplied mounting plate from the unit by inserting the blade of a small screwdriver into the locking tab release window see Diagram 2 and pressing it against the case locking tab see Diagram 1 while sliding the plate downward along the case back.
The installer should assume the responsibility of developing and offering a regular maintenance. Attach the case back to the mounting plate by sliding the keyhole slots in the case back down.
Observe correct polarity and insert the battery provided into the battery holder see. Got it, continue to print. Comments to this Manuals Your Name. The locking tab will click as the case back locks in place.
When a satisfactory location is found, remove the battery and proceed with installation. If qdemco wiring is to be used, feed it through the slot in the case back but do not connect. Don’t show me this message again.
The Multi-Point Universal Transmitter may have three contact loops connected to it.
Do not recharge, disassemble, heat above. Dispose of used batteries promptly.
The description that follows assumes that the unit adeemco be mounted adrmco shown in the diagrams. Replace battery only with: To print the manual completely, please, download it. Seller does not represent that the product s it sells may not be compromised or circumvented; that the product s will prevent any personal injury or property loss by burglary, robbery, fire or otherwise; or that the product s will in all cases provide adequate warning or protection.
This warranty replaces any previous warranties and is the only warranty made by Seller on this product s.
Honeywell ADEMCO 5817 User Manual
For UL installations, no contact in any of the loops may be more than 3 feet from sdemco transmitter. The Primary Loop has several DIP switch selectable options that determine its connection requirements, response, and transmission characteristics see DIP switch setting table on next page.
Enter text from picture: A built-in cover tamper switch is activated when the cover is removed. Page of 2 Go. For this application, the alignment guide strip along one edge of the plate serves no function and may be broken away, if desired.
Honeywell ADEMCO 5817 Installation And Setup Manual: Wiring Connections; Specifications
Disengage the supplied mounting plate from the unit by inserting the blade of a small. With the battery still not inserted, connect the loop wiring to the unit’s terminals see Diagram 2.
Add to my manuals Add. It is not necessary to program the transmitter IDs during installation. Seller’s obligation shall be limited to repairing or replacing, at its option, free of charge for materials or labor, any product s which is proved not in compliance with Seller’s specifications or proves defective in materials or workmanship under normal use and service.