+ Add to cart. Specification; Documents. Manufacturer. BENTEL. Part number. J Number of zones. 8. Zone expansion up to. Supply voltage. V AC. Fire Control Panel J – Fire Conventional Control 8 zones (expandable to 24 zones) BENTEL panel corresponding to EN54 standard. Each zone can. View and Download Bentel J installation manual online. The J and J Control panels provides the follo – wing features: 8 Supervised/Bypassable .
|Published (Last):||10 December 2007|
|PDF File Size:||15.7 Mb|
|ePub File Size:||16.7 Mb|
|Price:||Free* [*Free Regsitration Required]|
Installing Repeaters Installing the Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 and Security Systems Fire Control Systems. The delay countdown will follows. Remove the screws 4 and open the Control panel.
To print the manual completely, please, download it. Display Door screws Unless otherwise stated, the numbers in boldface in this Keyswitch Access Level 2. J Declaration of Conformity English.
Each detection zone is equipped with an alarm repeat output for selective alarm management in the event of fire. The J and J Control panels provides the bentdl – wing features: Button n Pre-extinguishment Phase n Manual Extinguishment If the programmed extinguishment conditions occur The Extinguishment Module can be activated from ma – programmed by your Installerbentwl Extinguishment nual call-points ask your Installer for details.
Connecting A Power Supply 60 and jumper connectors.
Bentel J424 Installation Manual
The J bdntel panel is also available with a backlit display, which shows all the information regarding the control panel status. Remove the screws 4 and open the Con- trol panel. PS Input of Extinguishment Mod. EN54 and EN approved with JEXT extinguishment module 8 controlled, balanced, bypassable input zones expandable to 24 by means of two 8 zone expanders Up to 32 devices can be connected to each zone but no more than in total: Module will generate the Pre-extinguishment phase which will be signalled by: Introduction 3k5 of IEC Once the operating parameters have been set up, they To Download several pages: PS Input of Extinguish.
Time option Key 0respectively, to increase or decre The Extinguishment Modules page will allow you to This section describes how to program the system from enrol and set up Extinguishment Modules, as follows. J42-8 the reverse locking supports 93 into their respective locations 94 as per Fig. Module for fire extinguishment purposes up to 2 Extin- Ack.
Enter text from picture: Don’t have an account? Page 10 Logic Extinguish.
BENTEL J INSTALLATION MANUAL Pdf Download.
These devices have been specially designed To activate an Alarm when the Control panel is in Z24 and the Test key simultaneously. Output Voltage of the Switching Power Supply to the indicated value.
Press Enter or Esc to confirm and go back to the Main menu. Related Manuals for Bentel J No related manuals.
Check24 on valmimisel
Operating principles This Normally-Open Output open-collector will: This easy-to-use control panel is protected by a lockable frontplate which allows operational access to authorized personnel only. Figure 15 Wiring diagram of 3 detectors with Normally-Open Outputs and a Call point with zero ohm contact resistan – ce: By pressing ‘print’ button you will print only current page. Expanders Modules must be installed befo- re mounting the Control panel to the wall.
BENTEL J424-8 Panel
To download a specific page: The device concerned has been restored Table 2 Event Descriptions Continues Page 32 Module for fire extinguishment purposes up to 2 Extin- Ack. Installing Repeaters Installing Repeaters Installing benntel Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 and Flat cable accessory item: Display Door screws Unless otherwise stated, beentel numbers in boldface in this Keyswitch Access Level 2 Page 15 Flat cable accessory item: The Silence button can be used during Access Le – vel 2 only.
This module provides written infor – long pause lasting 5 seconds ; Install the Extinguishment Module, as follows. Up to bntel A can circulate on the PR Output. Installing the Extinguishment Module observed. It has 8 zones main board and supports two JEXP8 expander modules, for a total of 24 zones and devices maximum 32 in each zone.