Manuals and User Guides for Panasonic CS-S10PKH. We have 1 Panasonic CS- S10PKH manual available for free PDF download: Service Manual. View and Download Panasonic CS-S10PKH service manual online. CS-S10PKH Air Conditioner pdf manual download. Also for: Cs-s13pkh, Cs-s15pkh. Panasonic CS-S10PKH Manual Online: Cs-s18pk Cs-s24pk. Indoor Electronic Controllers, Cross Flow Fan and Indoor Fan Motor Removal Procedures.
|Published (Last):||25 January 2016|
|PDF File Size:||6.5 Mb|
|ePub File Size:||20.40 Mb|
|Price:||Free* [*Free Regsitration Required]|
Then, operation will restart after 1 minute. The caution items stated here must be followed because these important contents are related to safety. Don’t have an account? It does not swing during fan motor stop.
Indoor Unit Outdoor Unit CS-S10PKH CS-S13PKH CS
Do not touch the sharp aluminum fins or edges of metal parts. Pull out to remove the drain hose from the discharge grille Figure 15 Hold both sides of the front grille and remove it by pulling up and toward yourself gently.
Powerful Mode Operation Figure 4 To remove discharge grille Pull out the main Outdoor fan will turns off 30 seconds after compressor stops to operate. It may generate toxic gas when the refrigerant contacts with fire.
Press the CHECK button on the remote control for about 1 second with a pointed object to transmit signal to main unit.
Refrigeration Cycle Diagram 5. There should not be any obstacles blocking the air circulation.
Cross flow fan Reminder: Refrigeration Cycle Diagram 5. Page 61 Remove the tapes and connect the power supply cord and connection cable between indoor unit and outdoor unit according to the diagram below. By default, the outdoor fan speed is set to Hi. Then pull the discharge grille downward gently to dismantle it Figure 5 Pull out to remove the drain hose from the discharge grille It may cause injury.
Please use a high temperature solder iron. The same diagnosis can be repeated by turning power on again. Be sure to connect the end of the charging hose with the push pin to the service port. The indoor unit fan stops temporarily and then starts to blow at minimum airflow for 30 seconds. SET Transmit check code and after 2 seconds return to normal mode. Do not modify the machine, part, material during repairing service.
PANASONIC CS-S10PKH SERVICE MANUAL Pdf Download.
Otherwise, it may cause electrical shock and fire in case equipment breakdown or insulation breakdown. Don’t have an account? Refrigeration Cycle System Powerful operation stops condition o When one of the following condition is satisfied, powerful operation stops: Putty or caulking compound 67 Please remind the customer to keep the operating instructions for future reference.
Then, operation will restart after 2 minutes. Figure 12 6. Location of Controls and Components If control board cover is not fixed perfectly, it will cause heat-up or fire at the connection point css terminal, fire or electrical shock.
Do not install the unit near the door way. Attach the control board cover back to the original position with screw. Total Running Current S10lkh Even if Fan Speed button is pressed, no signal is sent to the unit and no change on remote control display.
Do not touch outdoor unit air inlet and aluminium fin. Outdoor high pressure rise protection Cable connection to the power supply through Isolating Devices Disconnecting means.
Remove the control board cover by releasing the 2 hooks. Cooling Overload Control The normal outlet air temperature and pressure of the refrigeration cycle depends on various conditions, the standard values for them are shown in the table to the right.
Outdoor fan speed can be changed to Hi or SHi x10pkh to outdoor temperature. Outdoor fan turns on when compressor starts to operate. When installing at roof, please consider strong wind and earthquake. In order to achieve the suitable operation mode, the microcomputer maintains the set temperature by measuring the temperature of the environment and performing temperature shifting.
If electrical circuit capacity is not enough or defect found in electrical work, it will cause electrical shock or fire. Exploded View and Replacement Parts List Do not sit or step on the unit, you may fall down accidentally. Remove screw to remove terminal board complete.